AN OVERVIEW OF MEDM

Kenneth Evans, Jr., Argonne National Laboratory, Argonne, IL, USA

* Work supported by the U. S. Department of Energy, Office of Basic Energy Sciences, under Contract No . W-31-109-ENG-38.

Abstract

MEDM, which is derived from Motif Editor and

Display Manager, is the primary graphical user interface

to the EPICS control system and has also been used for

other control systems. MEDM has two modes of

operation, EDIT and EXECUTE. In its EDIT mode it

provides the drawing tools needed to design control

screens for operator interfaces. In its EXECUTE mode

it manages those screens to communicate with the

control system. MEDM provides a set of interface

objects that falls into three main categories: (1)

Monitors, such as text, meters, and plots; (2) Controllers,

such as buttons, menus, and sliders; and (3) Drawing

Objects, such as lines, rectangles, and images. Each of

these objects has many options, allowing for the

development of screens ranging from simple to quite

sophisticated. MEDM has been developed over the last

decade, primarily at Argonne National Laboratory, and

is a large, well tested, extensively used program. It runs

on most flavors of UNIX, VMS, and Windows

95/98/NT. It has been used to design thousands of

control screens, such as the one shown in Fig. 1, at the

Advanced Photon Source and other sites around the

world. This paper presents an overview of MEDM and

its features.

1 INTRODUCTION

This paper assumes the reader is

familiar with the Experimental Physics

and Industrial Control System (EPICS).

Further information on EPICS and

MEDM may be found in the extensive

online and printed EPICS documentation

[1]. MEDM is an X Windows program

that uses Motif, a standard collection of

widgets. (Widgets are X Windows

interface objects.) Its attractive look and

feel is derived from the three-dimensional

appearance of Motif. MEDM has been

designed for UNIX systems but will run

on VMS as well. It will run as native

code on Windows 95/98/NT, provided the

Exceed X Server and X libraries [2] are

used. MEDM has extensive help, both

menu-driven and context-sensitive, as well as a comprehensive reference manual. The

interactive help utilizes Netscape [3], which can be

controlled from within MEDM.

2 MEDM OBJECTS

MEDM supports a relatively small number of objects,

which are used as its building blocks in designing

control screens. These screens are also called displays.

The MEDM objects are listed in Table 1. In addition,

there are two special objects, the Display itself and the

Composite, which is a group of MEDM objects defined

either by grouping the objects in EDIT mode or by

Table 1: MEDM Objects

Graphics Monitors Controllers

Arc Bar Monitor Choice Button

Image Byte Monitor Menu

Line Cartesian Plot Message Button

Oval Meter Related Display

Polygon Scale Monitor Shell Command

Polyline Strip Chart Slider

Rectangle Text Monitor Text Entry

Text

Figure 1: Advanced Photon Source status display.

reading them from a file.  Each of these objects has
properties or attributes that can be specified by the
screen designer and in some cases modified by the user.

The objects range in complexity from the Graphics
objects to the relatively sophisticated Strip Chart and

Cartesian Plot.  Except for the Related Display and Shell

Command, they can all be attached to EPICS process
variables.  The Controllers and Monitors set or read the
values of the associated process variables, and the

Graphics objects determine their visibility (whether they
are drawn or not) or color from the values of the process
variables.  The visibility of Graphics objects is
calculated via an expression similar to that used in the

EPICS Calc record.  This expression can involve the
values of up to four process variables as well as other
properties, such as the limits or alarm status, of the main
process variable.  The visibility of the Composite can be
controlled in the same way as for the Graphics, allowing
displays to change dynamically.

       All of the Controllers are also Monitors; that is, they
reflect the current value of the process variable.  Some
objects are drawn on the display background.  Others are
implemented as widgets and have their own X windows.

Most of these widgets are MEDM custom widgets, but
some are standard Motif widgets.

        The Arc , Line , Oval , Polygon , Polyline , Rectangle ,
and Text  are geometrical shapes or text that are drawn
on the background of the display.

       The Image  is a Graphical Interchange Format (GIF)
image.  If the GIF file has more than one frame, the

Image may be set to animate or to have a particular
frame show based on a Calc expression similar to that
used for visibility.

       The Bar Monitor  is a filled horizontal or vertical bar
with optional decorations.  It may be used to make bar
graphs.

       The Byte Monitor  shows bit values and is used with
the EPICS mbbiDirect and mbboDirect records.

       The Cartesian Plot  displays one or more array
process variables or sequential values of single-valued
process variables on an XY plot.

       The Meter  shows its process variable as a meter with
a needle indicating the value.

       The Scale Monitor  shows the process variable as an
indicator mark on a horizontal or vertical scale.

       The Strip Chart  shows time traces of one or more
process variables on a strip chart plot.

       The Text Monitor  displays the value of a process
variable as text in one of several formats.  It is also
drawn on the display background.

       The Choice Button  is a Motif radio box widget with
radio toggle buttons.  It is used for ENUM process
variables, those that have specific values represented by
a set of character strings or integers.

       The Menu  is a Motif pulldown menu widget.  It is
also used for ENUM process variables.

The Message Button  is a Motif button that sends a
value to a process variable when pressed and/or released.

 The Related Display  is a Motif pulldown menu that
brings up other displays.  There is a macro capability to
replace keyword names in the display file with specified
values so one file can be used for similar items, for
example, different power supplies of the same type.

This object can also be hidden under a Graphics object ,
so that clicking on the graphics object activates another
display.

The Shell Command  is a Motif menu of commands
that are executed by the operating system as separate
processes from MEDM.  Special characters in the
command are replaced by things like the name of a
process variable or allow the user to complete the
command.

The Slider  is a Motif scale widget.  It allows changing
a process variable by dragging the slider on the
horizontal or vertical scale.

The Text Entry  is a Motif text widget.  It allows
changing the process variable by entering characters or
numbers.

3   EDIT MODE

In EDIT mode MEDM is essentially a drawing
program.  As such, it allows creating, positioning, and
sizing of the MEDM objects on the display.  It also
provides a means of changing the properties of the
objects, including assigning process variables to them.

MEDM has most of the features of a drawing program,
including undo, cut, copy, paste, raising, lowering,
grouping, spacing, alignment, centering, and snap-to-
grid as well as several features special to MEDM.  Much
of the editing is accomplished through three MEDM
palettes.

The Object Palette, shown in Fig. 2, is used to select
the type of a new object.  The name of the object pops
up as shown in the figure if the cursor is held over the
icon representing the object.  The type can also be
selected via the Edit Menu.  After selecting the type, the
object is created by dragging a rectangle of the desired
size on the display.

Figure 2: Object Palette with popup showing the
icon is for the Meter.

       The Resource Palette, shown in Fig. 3 for a Meter, is
used to change the properties of the object.  What
appears in the Resource Palette for a particular object
depends on what properties the object supports.  The
property choices may be specified through text boxes,
menus, a color selector, or buttons that bring up dialog
boxes.

       The color selector brings up the Color Palette, shown
in Fig. 4.  MEDM has a colormap consisting of 65
colors.  There is a default colormap, but each display
may have its own colormap, defined in its display file or
specified by the name of a separate colormap file.

                                           4   EXECUTE MODE

       In EXECUTE mode MEDM manages the connections
to all the process variables associated with all the objects
in all of the displays that it has open and also keeps the

MEDM objects updated with the latest values.  It
handles user input to change the values of the process
variables and interact with any of the MEDM objects.

       MEDM can manage one hundred or more displays at
the same time, depending on the complexity of the
displays and the power of the workstation on which it is
running.  There is a command line option that allows
new invocations of MEDM to pass their displays to an

already-running MEDM, then exit, avoiding a
proliferation of executables and providing efficiency.  It
also makes it easier to write scripts that bring up all the
necessary displays to operate a particular device such as
an accelerator ring.

There is a popup menu of options for the user in

EXECUTE mode.  The user can print or close the
display and can obtain extensive information about the
process variables associated with an MEDM object that
is selected with the cursor.  The resulting dialog box for
doing this is shown in Fig. 5.  The user can set the limits
of objects, such as the Meter or Bar Monitor, for which
limits are appropriate or set the precision (number of
decimal places) of numbers displaying in the object.

The user can obtain a list of all the currently managed
displays and can access an optional, configurable
submenu of custom commands.

5   REFERENCES

[1] http://www.aps.anl.gov/epics has extensive
information  on all parts of EPICS as well as links to
both the HTML and Postscript versions of the

MEDM Reference Manual.

[2] Exceed is a product of Hummingbird

Communications  Ltd., North York, Ontario, Canada.

[3] Netscape is a product of Netscape Communications

Corporation, Mountain View, CA.

      Figure 3: Resource Palette displaying the choices for

                                                                     a Meter.

         Figure 4: Color Palette showing the default colors.

Figure 5: PV Info dialog box.